Ultra-low temperature freezer in use process, if appear the condenser is not hot, refrigeration effect is poor, the phenomenon of frequent start, is likely is compressor compression failed;
If the cryogenic refrigerator motor does not start properly, humming, and shows the start of the compressor failed;
If not present other cryogenic refrigerator motor noise, via detecting its insulation resistance value is 0, winding resistance is very big, may be the compressor winding wire break.
This phenomenon mainly caused by a bad compressor.
by checking if not found evaporator frosting, and refrigerator condenser low temperature and high pressure pipe, at the same time detecting compressor operation current is very small, the situation may be caused by industrial ice machine
leakage completely, maintenance should check the industrial ice machine storage and related piping, find out the leakage parts for repair.
cryogenic refrigerator appeared when using intermittent or no refrigeration phenomenon, or heard not the voice of the refrigerant flow evaporator and condenser surface temperature is higher, these phenomena are often the cooling tube obstruction.
Maintenance should be according to its specific performance judgment refrigeration tube obstruction degree, and then take corresponding measures to eliminate.
cryogenic refrigeration function drops, half frost or not frosted evaporator happen, and on its oil and sand holes, can judge the fridge evaporator appeared leak or remaining oil.
Maintenance should be the first release industrial ice machine, and then a thorough cleaning.
Guangzhou Icesource Co., Ltd is willing to push up our sleeves and wade into unknown territory with equal parts fearlessness and optimism.
If you would like to learn more about ice maker machine cold room supplier, and other types, please be sure to visit Icesource . We can offer you top quality as well as cost saving price.
We are professional in manufacturing cold room supplier, and always emphasize the technology and quality during the producing procedure.
The key to cold room supplier is understanding where there is a problem or need in certain markets and knowing how to solve it.
Guangzhou Icesource Co., Ltd has a number of producing line for producing cold room supplier.