Screw water chiller or screw unit, the common failures and solutions, cold water vendors would arrange for you as follows:
a, exhaust temperature is too high,
Compression is larger;
The oil temperature is too high;
Breathe in serious overheating, or bypass valve leakage;
Lack of fuel injection quantity.
(1) to reduce the exhaust pressure, reduce the load.
2. Cleaning oil cooling, lower water temperature or increasing the amount of water.
(3) increase the amount of feed liquid, strengthen inspiratory insulation, check the by-pass pipe.
4. Check the oil pump and oil pipeline.
5. Overhaul the machine.
2, compressor running after automatic stop
Automatic protection Settings is not appropriate;
Control circuit fault;
(1) check and adjust the set value.
2. Check the circuit, eliminate the malfunction.
3. Check the reason and eliminate.
3, inspiratory pressure too low
Low evaporation temperature, heat transfer temperature difference;
Insufficient system industrial ice machine
For the liquid valve opening;
Back to the trachea way too much resistance;
The suction valve opening or failure;
Suction filter dirty or ice block.
1) overhaul evaporator, increase the refrigerant flow, reduce the compressor load.
(2) leakage, filling refrigerant.
(3) increase for liquid, check the line.
4. Open the suction valve or check valve head.
(5) cleaning filter, remove the moisture.
Currently there is a global trend growing. People are more conscious about ice maker machine and are seeking alternatives to traditional solutions.
Get ice maker machine cold room supplier from only reliable exporters, go to Icesource for more details.
To find a qualified at reasonable price, contact Guangzhou Icesource Co., Ltd at Icesource , a professional provider and tell them what you envision for your cold room supplier.