Industrial water-cooled and air-cooled industrial ice machine
points two kinds, the difference between the two lies in the industrial ice machine condensing way (
The cooling way)
The compressor exhaust pressure at work (
The high pressure)
Have a direct relationship with the cooling and inspiratory pressure (
The low pressure)
Will have a direct relationship with chilled water temperature.
outdoor temperature 32 ℃ in summer and well ventilated condition, the high pressure water cooled in 14 ~ 18 kg / ㎝ & sup2;
If belong to the normal range, super 22 Kg / ㎝ & sup2;
, the unit will protect jump stop;
High-pressure air cooled in 17 ~ 22 kg / ㎝ & sup2;
Belong to the normal range, if exceed 28 Kg / ㎝ & sup2;
Jump stop, will protect the crew.
compressor working at low voltage with the temperature of the chilled water and flow rate, general evaporator outlet for the 7 ℃, low voltage is 4 Kg / ㎝ & sup2;
, when the water is 15 ℃, low voltage is 4.
Or so, when the water is 20 ℃, low pressure for 5.
The left and right sides.
Is directly proportional to the compressor shut down when the pressure is also with the temperature, the summer is usually 10 ~ 11 Kg / ㎝ & sup2;
And winter is 8 ~ 9 Kg / ㎝ & sup2;
is a must have for anyone who appreciates ice maker machine to the greatest extent.
More about the most suitable , visit Icesource to get your offer!
The rising ice maker machine consciousness observed worldwide are expected to be key factors driving the demand for ice maker machine cold room