- Our Project
- Plate Ice Machine
- Bag Block Ice Machine
- Pure Ice Machine
- Block Ice Machine
- Hot Sale Products
- Cold Room
- Nugget ice machine
- Automatic Block Ice Machine
- Direct cooling block ice machine
- Tube Ice Machine
- Ball Ice Machine
- Flake Ice Machine
- Containerized Block Ice Machine
- Cube Ice Machine
Double the school libr absorption chiller circulation process
parallel process of double-effect lithium bromide refrigerator solution 'comes from the absorber dilute solution branch at the same time into the low temperature solution heat exchanger, heat exchanger, high temperature solution and then shunt into the high voltage generator, low voltage generator, at the same time, respectively, from the high voltage generator and low pressure generator of strong solution, respectively, into the high temperature solution heat exchanger and the low temperature solution heat exchanger, the last two stocks with strong solution into the absorber.
welding concentrations of double-effect lithium bromide industrial ice machine is a parallel process. Path for the high voltage generator solution process: point 2 low pressure dilute solution of pump pressure promoted to p by high temperature solution heat exchanger variable points to 10, and then enter the high voltage generator, by heating, cooling steam produced solution point 12 concentrated solution, lane lane solution heat exchanger in high temperature solution is cooled to 13 points, with the solution of low temperature heat exchanger of concentrated solution of mixed into the absorber, then mixed with part of the dilute solution of the absorber to nine points, flash to 9 PM.
in low voltage generator solution flow path for the 9: point 2 low pressure dilute solution of the pump pressure promoted to p, the low temperature solution heat exchanger to point 7, then through heating of condenser and low-pressure generator, high voltage generator in low voltage generator produces the cold extrusion of condensate water release heat and cold extrusion steam produced, solution point 4 of the concentrated solution, concentrated solution was cooled in the low temperature solution heat exchanger to 8 points, with the solution of heat exchanger out point of concentrated solution of mixed into the absorber, and then mixed with some dilute solution in the absorber to nine points, flash to 9 PM.
Guangzhou Icesource Co., Ltd is deemed as one of the leading provider of cold room supplier products in China.
Try out ice maker machine cold room supplier to beautify your ice maker machine. Visit Icesource to get your dreaming at a favorable price.
Guangzhou Icesource Co., Ltd's main technology of cold room supplier leads us to understand and utilize information correctly.
Overall, cold room supplier may be a great way for manufacturers to expand their use of technology, but the price could present a significant hurdle for some businesses.