- Our Project
- Plate Ice Machine
- Bag Block Ice Machine
- Pure Ice Machine
- Block Ice Machine
- Hot Sale Products
- Cold Room
- Nugget ice machine
- Automatic Block Ice Machine
- Direct cooling block ice machine
- Tube Ice Machine
- Ball Ice Machine
- Flake Ice Machine
- Containerized Block Ice Machine
- Cube Ice Machine
Different types of cold water type issued notice
1, the refrigeration system load = indoor load + + new wind load and heat load. If the air conditioning system is the total load estimate index calculated by the air conditioning load, the refrigeration system load total = air conditioning system load.
2, and the choice of electric drive water chillers, when a single air conditioning refrigerating capacity Q> 1163 kw, appropriate chooses centrifugal chiller: when Q = 580 - Is 1163 kw, appropriate chooses centrifugal or screw unit: when Q< 580 kw, appropriate chooses piston type water chiller. When the winter average temperature is higher than outdoor - Unit 10 ℃ when, can choose ReBengShi cold and hot bath water.
3, the electric refrigerator refrigeration system COP higher than absorption chiller thermal system s about more than three times. Consumption has a low to high order: centrifugal, screw and piston type, absorption. Therefore, only when the appropriate heat source, especially the places where waste heat or waste heat can be used, or lack of electricity place, appropriate chooses absorption refrigerating machine.
4, cooling mechanism to choose 2 - commonly Four advisable, small and medium size appropriate chooses 2 sets, can choose three larger, oversize can choose four. As spare unit to consider between and the possibility of rotation use. Machine room can adopt different capacity of the unit with a combination of solutions, to save energy.
5, choosing chillers pollution to the environment should be considered: one is the noise and vibration, to meet the requirements of the environment: the second is the harm of refrigerants of atmospheric ozone layer and the size of the greenhouse effect.
6, for the choice of the chiller sets should avoid as far as possible choose single units, in conditions allow, can choose two or more of the industrial ice machine, so don't consider the spare unit, and in the case of load changes, you can turn off part of the water industrial ice machine, save operating cost, can make the unit running under high COP value. Water chillers and chilled water pump can adopt the way of one to one correspondence, such as restricted by the size of the room, also can use more than one chiller with many sets of frozen water pump independent parallel connection Settings. This kind of arrangement is it more obvious advantages of simple and convenient, but this way should be paid attention to in the case of a part of the air conditioning cooling load, is part of the chiller is in a state of suspended.
Guangzhou Icesource Co., Ltd thinks that effective market design can improve liquidity, efficiency, and equity in markets.
Guangzhou Icesource Co., Ltd will continue to bring our industry nuances of style and approaches to cold room supplier which are consistent with our evolving aspirations.
The development of ice maker machine cold room supplier products has massive potential for expansion.