Snowflake Tube Ice Machine
is in use, often there will be some failures. How to solve them? Changliu Scientific Instruments summarized five common faults and their handling methods, hoping to provide customers with some references. 1. The compressor of the snowflake ice maker works, and the water pump never works (there is no tap water). Failure reason: the water pump is damaged or the scale inside the water pump is blocked. Treatment method: clean the water pump or replace it. 2. The compressor works, but does not cool down. Failure reason: refrigerant liquid leakage or two-way solenoid valve damage. Treatment method: After leak detection, add refrigerant or replace the solenoid valve 3. The compressor of Chongqing Snow Ice Maker has been working and cooling, and the water pump has been working and pumping water. The ice is getting thicker and thicker, but it cannot automatically enter the de-icing program to de-icing. Failure reason: The water temperature probe is faulty, which makes the intelligent control system unable to effectively sense the water temperature and work, misjudging the program error, or the controller failure. Treatment method: Use a multimeter to measure the resistance of the water temperature probe (when the water temperature in the water tank is close to 0, pull out the three-core wire in the control box and test the resistance of the two wires on both sides). If the resistance is above 27K, it is judged that the controller is broken and should be replaced. If the resistance is lower than 27K, it is necessary to disconnect any of the two wires and adjust the resistance to between 27K and 28K through a series resistor. 4. The water shortage lamp is on, but the machine does not automatically supply water. Failure reason: There is no water in the pipeline or the water inlet solenoid valve is faulty, and the valve does not open. Treatment method: check the water inflow of the pipeline, if there is no water, restart the machine after opening the waterway. If the water inlet solenoid valve is faulty, replace it. 5. The Chongqing Snow Ice Maker entered the deicing process (the water pump stopped working and the compressor stopped cooling), but the ice did not fall off. Failure reason: The two-way solenoid valve is damaged. Treatment method: Replace the solenoid valve body or outer coil.
The global market was valued at ice maker machine in ice maker machine and is expected to reach a market value of ice maker machine by ice maker machine, with a CAGR of ice maker machine during the forecast period.
To understand how efficiently works, go to Icesource for more information.
Guangzhou Icesource Co., Ltd deems cold room supplier as evolutionary rather than revolutionary. We've always had these 'social commerce' marketplaces in some form.